How to fix or reduce water heater condensation. Can it affect the water heater operation? Condensation is usually considered as the leak. Find out the reasons and symptoms for the worry-free heating.
One of the questions I've got from my readers is about water heater condensation. The users were complaining mostly after they've seen the puddle of water under their gas-powered heater - after coming back from a vacation, during the winter time, or once they purchased a brand-new unit.
The puddle of water below the heater is the first sign of the water heater condensation or leak. You might also find black or red granules on the main gas burner when the condensate was dripping on the hot surface (you will also hear a sizzling noise). Corrosion on the jacket or around the vent is also a sign that the condensate (moisture) was present there.
When natural gas or propane gas is burning inside the combustion chamber of your gas heater, the flue gases are released. They contain lots of moisture and when it is chilled below the "dew point", the condensate forms. The "dew point" is the temperature when the water vapor turns into a liquid.
The heater usually produces one-half gallon of moisture every hour of heater's operation, so according to the experts, condensation is a regular occurrence.
Today's heaters are producing even more condensate due to their high-efficient operation - condensation is usually noticeable when the efficiency is above 87.5%. High efficient heaters, including condensing models, are utilizing the heat from flue gases and transfer it to water.
As the temperature of the flue gases gets reduced, the water vapor turns into a liquid - condensate.
It is very simple to identify if there is condensation or not.
First, if there is some water under the heater, wipe it up.
Turn the gas control valve to the OFF position.
Wait for several hours to see is it wet again under the heater.
If no water means that the heater was condensing.
There are several reasons why water heater condensation occurs:
If you have one of the above situations that will cause the condensation, fix the problem by increasing the temperature of the incoming air, water or tank size. Proper, unobstructed venting is also important so the moisture can leave the heater easily. As the condensate is mildly acidic, and as it will corrode the steel vent, PVC and stainless steel vents are recommended, if applicable and required per code.
Problems associated with the water heater condensation:
Power Vent and Power Direct Vent heaters are equipped with the condensate drain, so the water vapor from the exhaust gases will roll down the PVC vent pipe and through the drain port out. The recommendation is to get a condensate drain kit for convenient draining, and metal drain pans to protect the room where the heater is installed.