Fixing the water heater noise such as popping, banging, sizzling, rumbling, and high pitch sounds. What causes the noisy water heater, troubleshooting tips, and how to avoid the problem.
Water heaters are expensive to buy, installation as well. To avoid future failures and costly service, it is recommended to maintain a heater regularly. Many problems can occur, so recognizing the symptoms and get the right instructions for the proper troubleshooting are mandatory if you want to DIY.
The most common problems are “no hot water”, “not enough hot water”, leaking and noise.
All water heaters, either electric or gas-powered, made by Rheem, AO Smith, Bradford White, Kenmore, GE, or any other manufacturer, could have problems associated with the noise, such as:
The most common reasons for pounding water heater noise are the mineral buildup at the bottom of the tank and water hammer. Water hammer occurs when water is flowing through the plumbing and stops suddenly. The first signs of this problem are the pounding noise, banging and thumping sounds, and vibration coming not from the heating unit but piping. The only fix of the water hammer and pounding noise is to install the water heater arrestor.
The sizzling noise coming from a water heater happens due to condensate leaking on the hot surface of the gas burner surface. The typical residential model will produce approximately one half-gallon of condensate during the hour of operation during the hour of operation.
The condensate is a regular occurrence of gas heaters as the flue gases carry lots of moisture, so when the condensate is dripping on the hot surface, it is normal to hear a sizzling noise.
Electric water heaters also make a sizzling sound when the heating elements are covered with the limescale, so water will boil water to steam as it is trapped next to the element.
Condensation usually stops when the heater reaches a temperature of 115 F.
If a sizzling sound happens due to a water leak, unfortunately, the repair is not easy, and it might require purchasing a new unit.
The popping sound inside the heater results from hard water and sediment buildup at the bottom of the tank and unit's components. The popping noise comes from the water trapped under the mineral deposits. The steam bubbles would develop under the sediments and explode, making such a sound.
The solution is to lower the water hardness and soften the water. Otherwise, if you don't do the recommended treatment (i.e., deliming or adding phosphoric acid), including the regular flushing and maintenance, the high water temperature will bring even more deposits.
Aluminum hydroxide is another reason for the popping noise. If the water supply has a relatively high PH and the heater is equipped with the aluminum anode rod, the chemical reaction will result in aluminum hydroxide (it looks like the green, blue or gray gel) at the bottom of the tank and on the anode rod.
Replacing the aluminum with the magnesium rod with flushing and deliming will eliminate or reduce the noise.
- Find Plumbers In Your Area -
Aluminum hydroxide gel in the heater's tank and mineral buildup is the same reasons for rumbling and crackling noise as seen in the previous problem with the popping noise. As the water is making its way thru the sediments, the rumbling sound is what you will hear.
Ticking water heater noise results from the pressure fluctuations in the plumbing system when flushing the toilet or using the water fixtures or expanding and contracting against the framing, or lose connections. The fluctuation can also be heard as the clicking or tapping noise.
The energy-efficient models are equipped with the heat traps so when the ball is rattling in the nipple, it produces this ticking noise also. If the heat traps are the cause of the sound, you can remove them without reducing the efficiency significantly.