Why checking the burner flame in water heaters is important? What should you do if the flame has a yellow, orange or blue glow? What are the most common problems if the gas is not burning correctly and how to avoid it? How does the normal flame color and shape look like?
Every gas-powered and tank-type water heater uses the gas burner located in the combustion chamber to heat water, pilot light or electrode to light the fire, and gas control valve to deliver natural or propane gas.
During the burning process, exhaust gases are vented out, either naturally (convection) or forced (electric blower). Therefore, tank-type water heaters are divided into atmospheric, power, direct and power direct models.
Most of the models have a viewport (opening) at the bottom of the unit where you can check the condition of the gas burner, how does the flame look like, and does it require any action or not.
Blue flame means that everything is OK and the air/gas mixture is in the correct ratio.
Yellow flame occurs when there is not enough air coming to the flame.
Orange or red flame happens when dust and other debris burn together with the gas.
Note: The orange flame doesn’t always indicate a problem, as it could last for a minute or two, and as the dust settles down, or gets burned, the flame goes back to blue glow.
Most of today's gas water heaters are equipped with the FVIR or Flammable Vapor Ignition Resistant technology and unique flame-arrestor feature, which prevents the flame and burning vapors to escape the combustion chamber, risking the open fire and potentially - explosion. Those water heaters that are subjected to this problem will show discoloration on the flame arrestor, which will require you to replace the unit.
Some gas water heaters are equipped with the air shutter, which allows you to adjust the air-gas mixture for proper burning. Too much of air will cause the burner flame to lift off the burner ports and burn with the noise. On the other side, if the flame becomes starved for air, the gas combustion becomes incomplete and will result in sooting.
The manually adjustable air shutter is usually found on the cast iron burners, while the steel burners utilize the self-adjusting air mixture.
The main indicators of the proper gas combustion are the stable blue flame or blue flame with the yellow inner cones (see the picture).
Proper operation requires sufficient air supply and ventilation, and the venting and exhaust system must not be blocked or have any obstructions. Fresh air is usually delivered through the provisions on the wall (atmospheric type water heater), which must be made per codes and manufacturer's instructions.
Correctly formed burner flame on the water heater also depends on the adequate draft in the draft hood, so regular check-up is recommended. One of the easiest ways is to use the match or candle flame, or smoke, put it close to the draft hood, and if the steady flame or smoke is drawn into the opening, the proper draft is established.
If the match flame flutters or is blown out, that means products of combustion are not going through the vent system correctly, but are escaping in the surrounding, contaminating the air. The changes are visible on the burner flame also, as the burner flame changes its color to yellow or orange and the stable pattern becomes unstable; is lazy or lifts off the ports...
Note: If you find the unstable flame in an old water heater and you are unsuccessful in identifying the problem, it might be worthwhile to get and install a new gas unit, especially if you have other gas appliance on the same line operating without problems.
Sooting is caused due to incomplete burning. Soot can be recognized as the black substance consisting mainly of carbon particles, that can accumulate on the heater’s elements, affecting its normal operation or even worse affect your health. Except for the natural gas burners, the problem can also occur in propane heaters, if the incorrect components (orifice) are used or gas regulators.
Keep in mind that the adequate supply of combustion and ventilating air must be provided without any obstructions. If there is an insufficient supply of air, the products of combustion will re-circulate, which will contaminate the surrounding air and cause the health issues.
As seen from the above text, one of the first signals of the improper gas combustion is the change in flame pattern, its color, shape, and height.
Visual checking of the main burner, burner flame, and pilot light should be done regularly, at least once in six months, followed by cleaning the dust and debris on the gas burner and combustion chamber.
Please describe the problem in details including the type of water heater and brand/model.
Click below to see contributions from other visitors to this page...
After changing gas water heater drain valve, heater started to smoke. Not rated yet
I had a leaky drain valve on my gas water heater, and had to replace it. It was quite the ordeal, and at one point, after the tank was emptied and drain …