What you should know when connecting a tankless water heater and home plumbing. Tips for DIY plumbing to prevent hot water problems, scalding, leaking, noise...
Plumbing installation of the tankless water heater must be done in such manner so the unit can operate properly and provide hot water on demand and in continuous flow; with leak-free connections and protected from freezing. The water heater life and performance depend on the properly designed plumbing system, water quality, water pressure and the environment where water is coming from, and the unit operates.
Every tankless water heater must be installed per manufacturer's instructions and local codes, correctly.
When talking about the plumbing system and water heating, tankless water heater must have the minimum water flow for its normal operation and use the pressure relief valve as the safety element. Installation of the following elements in the plumbing system or water heater is either mandatory and per codes, or recommended for better performance and safety.
In the closed water supply system, the thermal expansion tank must be part of the system, which will protect the unit from the excessive temperature and pressure build-up and will prevent the pressure relief valve from opening frequently due to the high pressure.
Water heaters are made to produce hot water, so that is why the protection from the scalding temperatures is important. The solution is to lower the temperature by mixing hot and cold water, or by installing the mixing valves, especially those with the low water resistance.
The recirculating pump can be used to provide instantaneous hot water delivery at the tap or shower. Also install a pressure meter on the inlet to prevent the boiling inside the water heater, which causes abnormal sounds and is decreasing the heat exchanger life.
If you live in the area with the hard water (high mineral deposits in plumbing), you might want to consider the installation of the sediment filters and water treatment devices.
In a case of the high water pressure from the municipality water pipeline, often cut-offs or water hammer, you might want to consider installation of the depressurizing valves, backflow preventers, check valves...
Each tankless unit in North America must have the pressure relief valve installed per ANSI, for all water-heating systems. When installing this valve, you must not plug it or install any reducing fittings, which will restrict the pressure valve from its normal operation. Furthermore, there should be no valves between the relief valve and a water heater.
The relief valve must be rated up to 150 psi and with the rating that exceeds the BTU input of the tankless water heater. It should be installed in the outlet line and close to the water heater. You must also install a discharge line from the relief valve to the appropriate drain to prevent any injuries from the scalding water. The discharge line must be able to withstand high temperatures and cannot exceed the maximum length (code regulation).
To ensure the proper work of the relief valve, it is recommended to test the valve annually. Keep in mind that periodic discharges might happen due to thermal expansion.
Many manufacturers include the isolation valves with the water heater. By installing the valves, you will be able to isolate the heater and perform any service and maintenance. They supposed to be installed on both cold and hot water line.
A manual control valve must be installed in the water inlet of the water heater and before it is connected to the plumbing. To make servicing easier, it is recommended to use unions on both hot and cold water line so that they can be simply disconnected.
Keep in mind when plumbing a tankless that the water lines and connections must be approved for use in potable water heating, and that includes copper, PVC, CPVC, PEX, and other types.
Union couplings or flexible pipe for connecting pipes should be installed to reduce the force applied to the piping. Avoid too many joints and keep the piping simple and as short as possible as the longer tubing means greater heat loss. The size of the pipes and fittings needs to be the same.
Make sure that there is no crossover, and the unit is leak-free. Ensure that there is minimum water pressure in the plumbing system (usually 50 psi). All tankless water heaters require a minimum water flow so the unit can activate, and that water flow is 0.4-0.5 gallons per minute.
I have seen many reviews and complaints about the slow hot water delivery, and this is why the recommendation is to check models that are equipped with the recirculation pumps, so you get hot water faster when a tap is open. A good example is Rinnai and its models from RUR series.
All the air and debris must be purged out of the water lines; otherwise, the damage to the unit might occur. Water filter cleaning should also be performed regularly.
When plumbing a gas-powered tankless water heater, make sure that non-metal pipes are kept away from the heater and its flue.