Error codes are the indicators of the problems inside the water heater. When the error code appears on the Bosch heater's LCD display, the reset button sometimes leads to an error removal, but if it doesn't work, the instructions below might help troubleshoot the problem:
The temperature of the flue gases is too high and is above 230 F. It is important to check for any gas leakage close to the gas combustion chamber and heat exchanger. Check if the limiter is operating and wiring is correctly linked to the control board and limiter. The element is located at the top-right corner of the unit.
Measure the resistance on wire harness; it must be between 115 and 120 ohms.
Check the backflow temperature sensor connection; it might be damaged, or it got short-circuited. It is located below the heat exchanger and ignition electrodes. Look for the diagnostic menu 1P and nC code.
The outlet temperature sensor reacts when the temperature is either below 36 F when the unit is protected from freezing temperatures, or above 210 F in a case of overheating due to the lime-scale deposits. Check the sensor and wiring. You might have to flush the unit to remove the mineral build-up.
Another error code associated with the outlet temperature sensor, but this time, the sensor is not sensing the expected output temperature. This is not an error code; it is a flashing status message that tells you to check; the wiring connection, gas pressure as it might be too low, voltage as it doesn't meet the required 120 VAC, the unit that might not be properly grounded or the issue with the control board.
The primary fan spins slowly when the water heater is working. Check the wiring connection on the fan and control board. The voltage must be 120 VAC and the element correctly grounded. Does the venting system meet the code and manufacturer requirements? Ensure that the gas pressure is as required because the low pressure leads to fan rotation problems.
No signal from the fan's rotational speed sensor. The sensor might be broken. Check the wire connection on the control board and fan. The voltage needs to be 120 VAC and adequately grounded. Ensure that a fan and control unit are not damaged.
Make sure that the water pressure is less than 150 PSI and a flow rate below 10 GPM. Check the wire connections on the water valve and control panel.
The temperature detected by the outlet temperature sensor is over 185 F. Ensure that the sensor is working correctly, and the wire connections are not loose. Another reason for the high temperature is the sediment build-up, so descaling is needed.
Check the sensor and wiring connections as this sensor is in charge of protecting the unit from freezing.
The unit will shut down if the temperature of the exhaust gases is above 194 F. Check and clean the heat exchangers if needed. Reduce the maximum power and water temperature.
The backflow temperature sensor reacts when the temperature is over 309 F. Check the vent pipes if they meet the code and requirements, look for damages and obstructions.
Check the wire connections on the sensor and control board. Ensure the venting system is per codes and instructions. Descale the unit if necessary.
The ionization electrodes are not making sparks when water is flowing. There are many reasons for this problem and here are some; low gas pressure, the fan speed is low, wire connections are loose, the air in the gas line, no gas.
Ionization electrode failure during water heating. The reasons might be; obstructed venting system, low gas pressure, and CO2 readings, the fan speed is too low.
The issue with the hardware or software. First, try to reset the error code; there might be confusion inside the computer. Check if the wire connections are properly linked to the computer board or the board is not damaged.
The problem is with the ionization rod at standby. Check connections to the electrodes; it should be securely connected. Other reason might include damaged element or control board.
The problem is with the gas valve circuit. Check the wire connections on the gas valve and control board. Measure the voltage on the wires when a water heater is ON… it should be 24 VDC. If the measurement is as specified, the gas valve is malfunctioning.
And what do you think about Bosch?
Click below to see contributions from other visitors to this page...